Standard Specification for Fabricated (Welded) Pipe Line Strainers (Above 150 psig and 150°F)
NORMA vydaná dňa 1.9.2016
Označenie normy: ASTM F1200-88(2016)
Dátum vydania normy: 1.9.2016
Kód tovaru: NS-651057
Počet strán: 4
Približná hmotnosť: 12 g (0.03 libier)
Krajina: Americká technická norma
Kategória: Technické normy ASTM
This specification covers welded pipe line strainers for use in applications above 150 psig and 150 F as well as in marine environment conditions. Strainers covered in this specification are classified into simplex, duplex (or multiplex), and automatic (self-cleaning) based on general construction. However, other bases for further classifying strainers are available: pressure ratings and types of port connection, port alignments relative to unit center lines, cover closures, valve types (in duplex), types of baskets or elements, materials of construction, and other design features. Strainers shall be manufactured by casting or forging or fabricated from plates, tubes, or pipes, with inlet and outlet connections requiring welding joined by butt welding. On the other hand, strainers made of carbon or low alloy steel shall be post-weld heat treated. The strainers shall undergo either hydrostatic or air test, while the welds shall be examined visually or radiographically. All tests shall conform to the requirements specified.
cast strainers, marine strainer, strainer, welded strainers ,, ICS Number Code 23.040.01 (Pipeline components in general. Pipelines)
1.1 This specification covers welded strainers in services above 150 psig or 150°F (1 MPa and 65°C). For welded strainers in services at or below these ratings and cast strainers, see Specification .
1.2 This specification provides the minimum requirements for the design fabrication, rating, marking, and testing of welded pipe line strainers for services above 0°F (−18°C).
1.3 Strainers manufactured to this specification are acceptable for use in the marine environment.
1.4 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
1.5 The following safety hazards caveat pertains only to the test methods portion, Section This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. , of this specification.
|2. Referenced Documents|
Chcete mať istotu, že používate len platné technické normy?
Ponúkame Vám riešenie, ktoré Vám zaistí mesačný prehľad o aktuálnosti noriem, ktoré používate.
Chcete vedieť viac informácií ? Pozrite sa na túto stránku.
Posledná aktualizácia: 2019-01-22 (Počet položiek: 2 213 684)
© Copyright 2019 NORMSERVIS s.r.o.